Carbon Filtration is used for several reasons. Its primary purpose is the reduction of chlorine to less than 0.1 ppm. Chorine can damage softener resins, reverse osmosis membranes, and mixed bed deionization resins. Activated carbon will also help control tastes and odors, provide organic and hazardous organic chemical reduction, and some particulate reduction. Activated carbon works through as an adsorption medium. When the carbon has been saturated with contaminants, it will need to be replaced with new carbon.
Filtration is the method of removing sediment particles from water by passing through various media. Media can be sand, Macrloite, filterAg, carbon, ceramic, paper, spun wound fibers, and fabric. There is a multitude of other filtration media available. Filtration effectiveness usually ranges between 100 microns to 0.1 microns depending on media and method selected.
Softening is the method of removing magnesium and calcium salts from water using an ion exchange process. As water passes through a column of selective cation resin, magnesium and calcium ions are removed and exchanged for a chemically equivalent amount of sodium ions. The cation resin is regenerated with sodium chlorides. Water Innovations (WI) applications utilize Kinetico’s unique non-electric valve. This valve incorporates an automatic, demand-initiated regeneration technology and duplex media tanks ensuring an uninterrupted supply of treated water.
Reverse Osmosis (RO) was the first crossflow membrane separation process to be widely commercialized. RO removes virtually all organic compounds and 90 to 99 percent of all ions. A large selection of reverse osmosis membranes is available to meet varying rejection requirements. RO can meet most water standards with a single-pass system and higher standards with a double-pass system. RO rejects 99.9 percent of viruses, bacteria, and pyrogens. Pressure, on the order of 200 to 1,000 psig (13.8 to 68.9 bar), is the driving force of the RO purification process.
Deionization is a method used for the removal of all ionized organic and inorganic minerals and salts from water, using a two-phase ion exchange procedure. First, the positively charged ions are removed by cation exchange resin in exchange for a chemically equivalent amount of hydrogen ions. Second, negatively charged ions are removed by anion exchange for a chemically equivalent amount of hydroxide ions. The hydrogen and hydroxide ions introduced in this process unite to form deionized water molecules (this process may also be termed demineralization).WI offers a wide variety of deionization systems to meet your needs from 5 gpm to 135 gpm.
Ultraviolet Disinfection is the utilization of ultraviolet wavelengths to sterilize water. Ultraviolet disinfection requires water that is virtually free of sediment and calcium or magnesium salts.
Distillation is the process by which a liquid, such as water; is converted into a vapor state by heating; then the vapor is cooled and condensed to the liquid state and collected. Distillation is used to remove dissolved solids and other impurities from water. Multiple distillations are required to produce the mineral free quality water that is routinely produced from a deionization process.
Deionization vs. Distillation
Deionization and distillation compete in many areas of application. They compete with each other on the basis of quality, convenience, and cost. Distillation removes the water from the minerals. Deionization removes the minerals from the water. Distillation kills organic matter by means of heat used in the distillation process. Deionization removes organic matter by means of filtration, carbon filtration, ultraviolet light, or some type of membrane filtration.
A single distillation process, such as the type normally used in producing bottled water, will produce a water quality of approximately 350,000 ohms. Triple distilled water in glass measures approximately 1,000,000 ohms. A mixed bed deionization system will produce water that measures in excess of 15,000,000 ohms. The total dissolved solid content of this water will measure approximately .03 to .04 parts per million of water. Distilled water can measure as high as 20 parts per million.
The last question to be addressed is sterilization by distillation. Sterilization is a process by which living organisms are destroyed. Sterilization is achieved in distilled water by use of the heat used in the distillation process. Deionized water is sterilized by use of an ultraviolet light. The ultraviolet light is used to kill living organisms that escape the chlorine used in the feed water. This does not mean either of these waters is considered sterile. In order to produce sterile water either of these waters must be exposed to some additional form of sterilization such as autoclaving the product.
Water Innovations offers several water treatment technologies, unique in the industry, for virtually any water quality concern.
At Water Innovations, Inc. we engineer solutions for wastewater treatment, closed loop water recycling and purification. We utilize ion exchange to produce the highest quality water with the lowest waste volume. Our Best-In-Class ion exchange systems utilize Smart Regeneration Control (SRC) delivering precise regeneration chemistry feeds, controlled regeneration rinse volume and grain set-point automatic adjustment. Click to learn more…
Water Innovations can be reached at firstname.lastname@example.org or by telephone at 760.466.7583